There are no inquiries yet.
For the control of independent 230 V AC drives via ABB i-bus? KNX.
The devices are designed for positioning blinds, roller shutters, awnings and other shading products as well as for controlling doors, windows and ventilation flaps. Additional auxiliary voltage is not needed.
To protect the drives, the output contacts are electromechanically locked against each other.
Push buttons are located at the front of the device to control the outputs e.g. during commissioning.
The current status of the output is displayed via LEDs.
spaceLYnk is the easiest way to build a complete Building Automation Solutions for commercial segments :
_ Complete Building Automation solution for Small and Medium building with a complete architecture including Light and Room Control (KNX, DALI Control), Metering (Modbus offer, Smartlink RTU and IP), and boiler management (SSL)
_ Complete Building Automation solution for Large Building with a complete architecture managed by SBO (BMS from Schneider Electric) and including Light and Room Control (KNX, DALI Control) and Metering (Modbus offer, Smartlink RTU and IP)
Generates an internal signal voltage for connecting four conventional push-buttons or floating contacts, and for direct connecting four low-current LEDs
The cores are 30 cm long and can be extended to max. 7.5 m. For installation in a conventional 60 mm switch box.
Device for switching and dimming four independent groups of luminaries with electronic ballasts (0 ? 10 V control input).
When combined with the light sensor LF/U 2.1 the device can be used as a 4-fold light controller for constant lightcontrol.